2021-10-18T16:53:46Z
https://www.heighpubs.org/oai/oai.php
oai:heighpubs.org:10.29328/journal.ijpra.1001040
2021-05-24
JPRA:VOL4
Working process of steam turbine and establishment of start-up model
Chao DongYongjian Sun<h2>Abstract</h2>
<p>In the research of steam turbine rotor, start-up optimization is a very key research problem. A series of start-up optimization research can greatly improve the start-up efficiency of steam turbine and the safety performance of the unit. The start-up optimization of steam turbine is inseparable from the analysis of the start-up process of steam turbine and the mathematical model of the startup process of steam turbine unit, because the optimization of steam turbine unit can be regarded as a function to find the optimal solution. This paper analyzes the start-up process of 300 MW steam turbine, analyzes the start-up process of steam turbine unit through the data used in the actual power plant, and gives the mathematical model of cold start-up of steam turbine according to the start-up process of steam turbine, so as to further study the start-up optimization of steam turbine. Finally, the optimization model is determined by several key parameters, which are three weight coefficients &alpha;1,&alpha;2,&alpha;3, the actual damage value Di&nbsp; and damage limit value Dlim, and the start-up time ti and total start-up time t0 of each stage.</p>
International Journal of Physics Research and Applications - Heighten Science Publications Corporation
2021-05-24
Research Articlehttps://www.heighpubs.org/jpra/ijpra-aid1040.phpenCopyright Â© Chao Dong et al.